6150-ALM-01, NFPA Alarm Panel
Mission Critical Reliability for In-building Coverage
NFPA code states that a dedicated alarm panel shall be provided within the fire command center to annunciate the status of all RF emitting devices and system component locations. The monitoring panel shall provide visual and labeled indications of the alarms.
The 6150-ALM-01, NFPA Alarm Panel will provide a visual display of the required Alarms for a single booster to meet NFPA standards. The annunciations on the alarm panel are 5 Bicolor LEDS (Green=No Alarm, Red=Alarm), dedicated to the 5 failure modes required by the NFPA code. The Bird NFPA Alarm Panel can be powered with the Battery Backup Unit or any other DC power source from 12 to 24 VDC. Alarm triggers are through Form C Contacts on the Booster.
The unit has an integrated battery charger and monitor system that maintains peak battery level when the main power source is present. The system provides LED status indicators and auxiliary alarm connections for remote monitoring. When used in conjunction with a Rescueline signal booster, the battery backup system provides a fully compliant solution to NFPA72, NFPA1221, or IFC.
- Alarm Input: Form C Dry contacts Normally Closed = Green
- Power Input: External DC supply (12~24 V, 100 mA)
- Alarm Display: LED
- Alarms Displayed: FAC Power Failure, Battery Charger Failure, Battery <30% remaining, Donor Antenna Failure, Booster Failure
- Enclosure: NEMA 4, Red